The MAT3 DALI module, equipped with sophisticated microprocessor module, is pre-programmed to carry out testing automatically. Connecting MAT3 module to emergency kit predisposed, obtain a localized system which information, on the functionality, are provided by three-colour led, positioned on the lamp.
MAT3 The module is designed to be connected via "two wire DALI BUS" (1) to a central control DALI. The result is a centralized system for full supervision of the whole system.
Complying with IEC 62386-202
Every 7 days it carry out a short test (about 30 seconds) on the function for lamp.
Every 12 weeks it carry out a test (1 or 3 hours) to check battery capacity.
Routine test starts when kit is supplied and resetted itself removing mains supply and battery.
|Yellow Blinking||Battery charging:|
– for 24 hours after installation, after at least 10’ black-out, or after full discarge
|Green Blinking||Test in progress:|
– single blink, lamp test
– double blink, battery test
|Green Permanent||All ok|
|Red Blinking||Test in progress:|
– Single blink, lamp fault
– Double blink, battery fault